Precautions while using UPS
Replace covers and panels as required. Power up the system in off line mode with the output breaker remaining off and the batteries still isolated, in accordance with operating instructions. Load program any software parameters as required, setting the desired output voltage. Using the appropriate safety precautions and where applicable and practical to do so.